Deep Well Submersible Pump InstallationTime of issue : 2019- 05-29
Use a special splint to clamp the short tube on the upper part of the submersible pump, start the lifting equipment, slowly lift the submersible pump and gently put it into the well bore
What are the preparations before installing the submersible pumpTime of issue : 2019- 05-29
Select a submersible pump with a suitable head. The actual required head of the submersible pump is consistent with the rated head of the pump. The actual required head is the sum of the downhole head
Classification and characteristics of deep well submersible pumpTime of issue : 2019- 05-29
The main feature of the submersible pump is that the pump and the motor are connected by a coupling, and the pump set has an elongated shape, so it can pump the water from the bottom of certain diameter deep well
What is the reason for the deep well submersible pump drop into the well ?Time of issue : 2019- 05-29
Mistakes due to installation technology. It is a technically strong mechanical installation to install deep well submersible pump. If the installer is unfamiliar with the performance and construction of the pump
What is the content of regular inspection and repair of the submersible pump?Time of issue : 2019- 05-29
Regularly check the insulation resistance of the record. Use a 500 volt megger to periodically measure and record the insulation resistance of the pump windings to the casing.
Do you know how to calculate the power and power consumption?Time of issue : 2019- 05-28
We know the flow rate (m3/h) and head (m) for deep well submersible pump we need, how do we calculate the required power for the submersible pump?
Precautions for hot water Submersible pumpTime of issue : 2019- 05-28
Qualified power supply, cable and starting equipment (such as air switch and auto-decompression start-up box) must be used as required. The starting equipment should have short-circuit
Deep well submersible pump use and post maintenanceTime of issue : 2019- 05-02
After install the submersible pump, we should check the insulation resistance and three-phase conduction from the switch, check the instrument and the starting device. If there is no problem, we can start and test the motor. After starting, observe the instrument indication